12-08-2009 09:37 AM
01-08-2009 05:20 PM
01-08-2009 10:10 AM
Tech1 provides a good simple process. However, please remember that lockout is specifically defined as an action that someone without a key cannot undo. And tagout should go along with it. Energizing the battery charger and releasing the emergency stop are easy enough to undo for someone else without thinking too much about why they were de-energized and pressed to begin with.
LOCKOUT = only the person who locked it can unlock it
TAGOUT = all others can see who locked it and why
11-24-2008 12:54 PM
The best way to lock a generator depend on three major factors
a) Type of maintenance needed carried out.
b) Type of starter (i.e. Is it electrical or pneumatic starter)
c) Type of start up configuration (i.e. Is it manual start/Auto local or Auto dead buss configured from remote)
When this has being achieved the following points of isolations could be done:
1. Isolate starter motor power or isolate power source to control panel and lockout.
2. Isolate start air or gas supply valve to starter motor and lockout.
3. Isolate fuel gas supply valve to engine and lockout
4. Isolate generator main power breaker at generator skid and switch room and lockout with a safety padlock
Note: Padlocks for Isolations must be secured according to the electrical safety rules governing the said generator.
10-23-2008 05:09 PM
We also lockout the fuel supply and PT if there is one for the unit.
Four total as a minimum
1) Unit breaker
3) Fuel valve
4) Battery disconnect
Also the other auxiliaries as mentioned, block heater, pan heater. Also air supply valve if there is an air start.
10-22-2008 12:51 PM