Thank you for you answer, ı changed the Cdvr, the problem was solved. But it is weird that the generator is running with bad cdvr for four hours than shut down, did you faced this situation like that? Also can ı see the cdvr failure cause by connecting with pc program?
Hello everyone We have a g3512 generator, the generator starting well, and working almost a hour, after that the output voltage drop suddenly, ı check permanent magnet fuses, they seems well. İs there any suggest to solve this problem?